Water flow rate 280M3/H
Inlet water temp. 37℃
Outelt water temp. 32℃
Wet-bulb temp. 28℃
The approach 4℃( Difference between cold water temp.and entering air wet-bulb temp.)
The cooling range 5℃
( Difference between hot water temp.and cold water temp.)
B SELECTION SOLUTION
1)shift the approach of 4 ℃ horizontally to find the intersecting point A with the 5 ℃ cooling range curve.
2)Trace up the point A vertically to find the intersecting
point B with 28 ℃ ambient wetbulb temp. ciuve.
3)Shift the point b to the right to find the intersecting
point C with the 280M3/H water flow rate.
4)Because the point C falls between the curves of 300 and
250,the selection is model 300.
1)In the interest of technological puogress, all products are
subject to design and/or material change without notice.
2)We can design and suply special cooling tower for customer.
3)Standard design condition Inlet water temp.37 ℃ outlet water temp.32 ℃ Wet-bulb temp.32 ℃ wet-bulb temp.28 ℃ Air pressure 9.94×104pa